[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
Re: pig in overdrive...
Original poster: "Jim Lux by way of Terry Fritz <twftesla-at-uswest-dot-net>" <jimlux-at-earthlink-dot-net>
The insulation is probably good for substantially more (check the BIL rating
on the nameplate). What won't necessarily be good for more voltage is the
core. It might saturate. You can probably run 10-20% overvoltage without
any problem (i.e. 48 volts over the nominal 240, or 288V), but 20% is
getting pretty near the edge. You can experimentally check this by running
it with no secondary load and looking at the current in the primary as you
raise the voltage. If you plot the current as a function of voltage, you'll
get a straight line up until the core starts to saturate, at which point,
the current will start to climb faster.
If you've got two identical transformers, paralleling is no problem. If
they aren't identical, then you'll need some sort of "equalizing"
transformer between the outputs to account for the different voltages or
----- Original Message -----
From: "Tesla list" <tesla-at-pupman-dot-com>
Sent: Sunday, February 25, 2001 7:20 PM
Subject: pig in overdrive...
> Original poster: "BunnyKiller by way of Terry Fritz <twftesla-at-uswest-dot-net>"
> Hi All...
> been kicking around an idea of supplying about 300-325V to a 10KVA piggie
> 14.4KV/240V type)
> at 14.4KV the peak to peak is about 20KV and at 300V in we should see
> about 25KV peak to peak
> on the output side... do yall think the insulation on the hi volt side
> good for 25KV????
> at present i have run the voltage up to 280V in via variac with no
> noticable side effects (
> other than longer streamers ;) )
> also .. has anyone here paralleled the output side of 2 10KVA piggies??
> for a 20KVA setup)
> thinkin again...
> Scot D